North American Network Operators Group|
Date Prev | Date Next | Date Index | Thread Index | Author Index | Historical
Re: Hot weather and power outages continue
Brandon Galbraith wrote:
My assumption is that it means "it isn't going to keep things cold, but it will keep the air flowing to prevent a 'server sauna'".
On 7/25/06, Sam Stickland <sam_mailinglists@xxxxxxxxxxxxxx> wrote:
> -----Original Message----- > From: owner-nanog@xxxxxxxxx [mailto:owner-nanog@xxxxxxxxx] On Behalf Of > Sean Donelan > Sent: 24 July 2006 13:27 > To: nanog@xxxxxxxxx > Subject: Re: Hot weather and power outages continue
> I've always been a fan of being able to force 100% economizer and chiller > loop bypass emergency operation; it won't keep you "cool" but will help > keep your data center from turning into an Easy-Bake Oven(tm). But that > failure operating mode is rarely part of the standard HVAC programming.
When I was in charge of such things, there was a way to circulate evaporator tower water n the chilled water loop to remove some of the heat, if you had enough power to run the two pumps.
Ex turpi causa non oritur actio