North American Network Operators Group|
Date Prev | Date Next |
Date Index |
Thread Index |
Author Index |
Re: San Francisco Power Outage
- From: Brandon Galbraith
- Date: Wed Jul 25 01:28:41 2007
- Dkim-signature: a=rsa-sha1; c=relaxed/relaxed; d=gmail.com; s=beta; h=domainkey-signature:received:received:message-id:date:from:to:subject:cc:in-reply-to:mime-version:content-type:references; b=MIi8Zmh8dsb/VlJk8jjrncNjx65j434q7TM1ZhQyA8U+drCB3LJPt2C+KRR+G/Ya+9rB8k1IzdjBa+pSQOEf4mQzxMWjBQCtH9zlU2g/doaUwlve+/PNcKe9CEcK2l9vS29ktMMN0OcEzHYODLBEHkYHAbI8KmtVYdKX55DXbwo=
- Domainkey-signature: a=rsa-sha1; c=nofws; d=gmail.com; s=beta; h=received:message-id:date:from:to:subject:cc:in-reply-to:mime-version:content-type:references; b=MY8Ig+eH1A7fK3gHrtU0FgveVrS7KsG3iU7gD7M1JA85vPYg8tTFqp7WUErbQLXsnGQHnUJhHcN5MTL/tMFsMe0AUfZqKjk9hG90jBcIR38Yad5f5bXU9mpVFfZoHvlcbqIrefJylSZ+1hZFy7nuTwTx0AdY/Oz0kfkJzUEwniE=
On 7/24/07, Owen DeLong <owen@xxxxxxxxxx> wrote:
On Jul 24, 2007, at 4:57 PM, Patrick Giagnocavo wrote:
I have no idea what the root cause of today's outage is. I will be
interested in hearing from any credible source as to any actual details,
but, I'm betting that right now, any such credible source is a bit busy.
It appears that 365 is using the Hytec Continuous Power System [
http://hitec.pageprocessor.nl/p3.php?RubriekID=2016], which is a motor, generator, flywheel, clutch, and Diesel engine all on the same shaft. They don't use batteries.
If the flywheels spent their energy before the generators came online, they don't have the ability to start the generators up without utility power (unless they purchased the Dark Start option, which is simply extra batteries).